For more detail on this Instruction Manual revision, please refer to the VeriSafe™ Safety Notice from January 18, 2018.
The VeriSafe™ AVT Instruction Manual is being updated to provide important safety information. A warning was added to the Safety Information section:
“If a Sensor Lead separates from the termination point to the power conductor and contacts a low impedance path to ground, the connectivity test can be defeated resulting in a false absence of voltage indication. Ensure that all sensor leads are terminated properly and secured to the power conductor or other nearby rigid feature to prevent movement if the termination fails to remain intact.”
A section was also added in the installation considerations with further detail.